Method 1: drying method
This method is to discharge water when the temperature of boiler water drops to 100-120 ℃ when the boiler is shut down. When the water is exhausted, the boiler inner surface is dried by using the residual heat in the furnace, igniting a slight fire or introducing hot air into the furnace.
Method 2: drying agent method
The desiccant method is to drain the water in the boiler when the temperature of the boiler water drops to 100 ~ 120 ℃ after the boiler is out of service. The metal surface is dried by using the residual heat in the furnace, and the scale and water slag deposited in the boiler water system are cleaned up. Then the desiccant is put into the boiler to keep the metal surface dry without corrosion. The commonly used desiccants are: anhydrous calcium chloride, quicklime and silica gel
Method 3: wet maintenance
Wet maintenance is generally applicable to the maintenance of boilers whose shutdown time is less than one month. After the boiler is shut down, the boiler water shall be drained according to the specified time, and the scale, water slag and ash shall be cleaned up.
Method 4: pressure maintenance
Xinxiang oil and gas-fired boiler manufacturers believe that it is suitable for production of standby boilers or boilers that are out of service for a short period of time less than one week. After shutdown, drain the boiler water, clean up the scale and water slag in the furnace, and add qualified softened water again.
Heat the boiler water regularly with small fire or steam from adjacent boilers to keep the boiler water temperature in the boiler at + 10 ℃ in summer and keep the boiler water from freezing in winter. Close the vent valve, drain valve and drain valve to prevent water leakage.
Method 5: thermal method
This method is used to stop the boiler within 10 days. The method is to install a water tank above the drum and connect the pipe with the drum. After the boiler is shut down, it is filled with water excluding peroxide, and most of the water tank is full of water. The water tank is heated by external steam to keep the water in boiling state. The key points of timely review after class are applicable to this link, and the following points must be paid attention to:
Thank you for your reading. This article is from Shandong gas fired boiler. For more information and questions, please click: We will continue to work hard to provide services for you, thank you for your support!